0061 RF Occupancy Or Vacancy Sensor User Guide Lutron Electronics
Seek advice from that product’s set up sheet for directions. Twist and remove mounting bracket to insert battery. Product Description Lutron’s ceiling-mounted Occupancy Sensors are wireless, battery-powered, passive infrared (PIR) gadgets that routinely control lights via RF communication with a dimming or switching device. These Sensors detect the heat from people transferring within an space to find out when the area is occupied. The Sensors then transmit the appropriate commands to the associated dimming or switching gadget to show the lights on or off robotically, offering both comfort and exceptional vitality financial savings. Sensor does not perform satisfactorily from this location, it may be moved to 1.4 Ifanother location by pulling the Sensor straight down and repeating steps 1.3 and 1.4. 1.5 If the Sensor’s performance is passable, it must be completely attached to the ceiling tile, as described in part G. Permanent Mounting. Momentary Strong Ceiling Mounting Use this procedure if the Sensor will be mounted on a solid, continuous ceiling surface corresponding to drywall, plaster, concrete, or wooden. Two 3M™ Command™ adhesive strips are supplied for temporarily mounting and testing the Sensor on easy, strong ceiling surfaces. These strips are designed for straightforward, damagefree removing and will not be reusable. These strips should not be used for completely mounting the Sensor (see section G. Everlasting Mounting ). Fastidiously follow the removal instructions below to ensure the ceiling is just not damaged throughout removal. Note: Don't use the adhesive strips on ceiling tiles, as they may possible cause damage to the tile upon removing. Simple-to-comply with Directions Set-Up To ensure that the Sensor to function correctly, it must first be set up with a corresponding dimming or switching machine. The process for setting up a Sensor with a Maestro Wireless® (MRF2- only) Dimmer or Electronic Swap is detailed below. P/N 041-172a 2.1 Peel the purple "Command Strips" liner off of one of the adhesive strips and apply the strip to the flat side of the mounting bracket as proven within the diagram. Notice: Don't cover the bracket’s screw holes as a result of they are going to be used to mark screw gap places on the ceiling. Setting up a Sensor with a Maestro Wireless Dimmer or Digital Swap Dimmer Key Options · Low Upkeep. 10-12 months battery life. Handy low-battery indicator. · Multiple Units. Up to three Sensors can work together to manage lights for broader protection in giant spaces. Every Sensor could also be added to as much as 10 receiving gadgets. Sensor Operation Occupancy Version - The Sensor will routinely flip the lights on when the house is occupied and robotically flip the lights off after the space is vacated. The Sensor will routinely turn the lights off after the space is vacated. There's a built-in 15-second vacancy grace interval that begins when the lights are mechanically turned off, throughout which the lights will automatically flip back on in response to movement. This grace interval is supplied as a safety and comfort characteristic within the occasion that the lights flip off while the room continues to be occupied, in order that the person doesn't need to manually turn the lights again on. After 15 seconds, the grace interval expires and the lights must be manually turned on. This Sensor is part of a system and can't be used to manage a load with no suitable dimming or switching gadget. Discuss with the instruction sheets of the receiving device(s) for set up information. The Sensor could also be put in as much as 60 ft (18.3 m) away from the related dimming or switching device(s) if they're in direct line of sight. If there are partitions or other barriers between the Sensor and receiving system(s), the Sensor should be situated inside 30 ft (9.1 m). Warning: This product must not be used to control equipment which could create hazardous conditions, similar to entrapment, if operated accidentally. Sensor in a location where it has a broad view outdoors the meant area. If that is unavoidable, the lens can be masked to block the view of undesired areas (refer to section I. Lens Masking). This warranty is in lieu of all other categorical warranties, and the implied guarantee of merchantability is limited to at least one year from buy. This guarantee doesn't cowl the price of set up, removal or reinstallation, or harm resulting from misuse, abuse, or damage from improper wiring or set up. This guarantee does not cowl incidental or consequential damages. LUTRON’S Liability ON ANY Claim FOR DAMAGES ARISING OUT OF OR IN CONNECTION WITH THE MANUFACTURE, SALE, Installation, Delivery, OR USE OF THE UNIT SHALL Never EXCEED THE PURCHASE Worth OF THE UNIT. This warranty gives you particular legal rights, and you could have other rights which differ from state to state. Some states don't allow the exclusion or limitation of incidental or consequential damages, or limitation on how lengthy an implied warranty may final, so the above limitations might not apply to you. Patents pending. Lutron, Maestro Wireless, and the Sunburst logo are registered trademarks and Radio Powr Savr is a trademark of Lutron Electronics Co., Inc. ANSI is a registered trademark of the American National Standards Institute. IEC is a trademark of the Worldwide Electrotechnical Commission. Made and printed within the U.S.A. 25/09/09 P/N 041-172 Rev. A eight ft (2.4 m) 18 x 18 ft (5.5 x 5.5 m) 13 ft (4.0 m) 9 ft (2.7 m) 20 x 20 ft (6.1 x 6.1 m) 14.5 ft (4.Four m) 10 ft (3.0 m) 22 x 22 ft (6.7 x 6.7 m) 16 ft (4.9 m) 12 ft (3.7 m) 26 x 26 ft (7.9 x 7.9 m) 19 ft (5.8 m) Non permanent Mounting Strategies 1.1 1.2 Insert the ceiling tile mounting wire by way of the two smaller holes within the mounting bracket and replace the mounting bracket. Mount Sensor to a ceiling tile by inserting the wire legs via the tile, ensuring the Sensor is flush to the tile. Notice: Don't twist wire legs together. 1.2 After the Sensor has been quickly mounted, go away the Sensor in place on the tile and either take the tile down or remove an adjoining tile to gain access to the legs of the mounting wire on the back of the tile. Low Exercise: That is probably the most sensitive setting and can detect very slight motions. This is the beneficial setting, as it would work nicely for nearly all applications. It is right for spaces where occupants will often be seated for lengthy durations of time. Twist the wire legs collectively tightly so the mounting bracket remains snug in opposition to the tile. This setting is barely less delicate than the Low Activity setting and can be utilized for spaces that expertise regular activity. That is the least delicate setting and can be used for spaces that can usually only experience massive motions, akin to foot traffic. The Low Exercise setting is the default and will perform finest for most applications. Rarely, if the Sensor is placed close to exterior noise sources corresponding to heating vents, air conditioning vents, or light bulbs, it may flip the lights on with out occupancy or keep the lights on too long after vacancy. If this occurs, changing the sensitivity to Medium Activity or High Exercise should resolve the problem. Change the tile. Everlasting Stable Ceiling Mounting 2.1 2.2 2.3 Superior Set-Up Operation The superior set-up is accessed by utilizing the buttons on the again of the Sensor. Drill two 3/sixteen in (4.6 mm) pilot holes for the provided screw anchors. Press the anchors into the holes and faucet flush with a hammer. To display the present setting, press and release the specified button. An LED will illuminate briefly, indicating the current setting. Place the flat aspect of the mounting bracket against the ceiling and set up the two provided screws utilizing a hand screwdriver. To regulate a setting, press and hold the specified button until the LED corresponding to the current setting begins flashing rapidly, indicating the setting can now be adjusted. Each subsequent button press of less than 2 seconds will increment the mode to the next available setting. Urgent any of the opposite buttons will don't have any impact. To save lots of the selected setting, press and hold the button till the LED turns on stable, indicating the saved setting. During the adjustment procedure, if there isn't any activity for 30 seconds, the LEDs will flip off and no settings will likely be saved. Notice: Do not over-tighten. 2.Four Attach the Sensor to the mounting bracket by inserting and twisting in a clockwise route until the Sensor locks into place. To remove the bracket from the ceiling, grasp the removal tab on the adhesive strip and pull the tab VERY SLOWLY straight throughout the ceiling, stretching the strip until the bracket releases from the ceiling. Discard the strip. By no means pull the strip at an angle, as it could break or harm the ceiling surface. Observe: Do not pull at an angle. Lens Masking (Elective) At any time when attainable, the Sensor must be installed in a location where it can not simply see into areas outside the supposed area, comparable to hallways or adjoining rooms. If this situation can't be avoided, parts of the lens may be masked with the supplied labels to block the Sensor’s view of the undesired areas. It is suggested to remove the Sensor from the mounting bracket before applying Superior Set-Up (Non-obligatory) the masking labels. The Sensor options a number of superior set-up modes. For nearly all of installations, the default settings will provide one of the best performance and you won't need to make the most of the advanced set-up. The Occupancy version of the Sensor has three adjustable superior set-up modes: Timeout, Auto-On, and Sensitivity. The Vacancy-Solely model has solely two modes (Auto-On not accessible). The default settings are listed below. The Sensor may be screwed onto the mounting bracket in several different orientations. Make sure to notice the Sensor’s orientation before taking it down and replace the Sensor in the identical orientation to make sure the meant space will get blocked. Outer lens sections correspond to the detection areas furthest away from the Sensor, while internal sections correspond to regions closer to the Sensor. Be careful when making use of the labels to avoid creating gaps between adjoining masked sections. The Sensor might detect motion through inadvertent gaps. At all times (Occupancy version only) Timeout 30 min 15 min 5 min Auto-On At all times Low light Disable Activity Timeout 30 min 15 min 5 min Superior Set-Up Modes Auto-On All the time Low light Disable Activity Activity: Low Activity Lens sections proven in white are masked with labels Timeout The Sensor will turn the lights off if no movement happens throughout the timeout interval. There are three available timeout settings: 5, 15, and 30 minutes. Lens Mask Lens sections shown in gray have not been masked Auto-On The computerized-on functionality of the Sensor can be adjusted to manage how the lights respond upon initial occupancy. There are three available settings: At all times, Low gentle, and Disable. All the time: The lights will all the time activate. Testing Sensor Coverage With the Sensor mounted on the ceiling, press and release the "Test: Sensor" button on the entrance of the system. The lens will glow briefly, indicating the check mode has been entered. Be aware: There is a warm-up interval of roughly forty seconds after the batteries are put in earlier than the take a look at mode could be activated. If the button is pressed throughout this time, the lens will flash continuously until the warm-up interval is complete, and then the check mode will be automatically entered. Affirm the coverage space by walking via the house and observing the lens. The lens will glow stable each time movement is detected. If the lens stays off during motion, the Sensor can't detect motion at that location. Press and launch the "Test: Sensor" button once more to exit the test mode. If the button is not pressed, the test mode will mechanically day out quarter-hour after being enabled, or 5 minutes after the final detected movement if the room is vacated. If the Sensor has vital trouble detecting movement throughout the check, it needs to be moved to another location and retested. If the Sensor still has poor detection from the brand new location, refer to the Troubleshooting part. Momentary Drop Ceiling Mounting Use this procedure if the Sensor can be mounted on a ceiling tile. The ceiling tile mounting wire is supplied for both short-term and everlasting mounting of the Sensor to drop ceilings composed of multiple tiles. It's designed to allow short-term mounting, testing, and repositioning (if needed) of the Sensor with out damaging a ceiling tile. Once the Sensor’s last position has been chosen, the mounting wire can be twisted to lock the Sensor in place permanently. If the Sensor protection and wireless communication exams have been successfully accomplished, use the mounting bracket as a template to mark the screw gap places with a pencil. Note: Pull very slowly. Max. Room Dimensions Radius of Coverage for Complete Coverage at Ground If you are unsure about appropriately positioning the Sensor, the following non permanent mounting and testing procedures are really helpful to verify correct performance earlier than permanently putting in the Sensor. Sensor’s detection range relies on the ceiling height, as proven in the desk beneath. Notice: Don't disassemble, crush, puncture, or incinerate the batteries. Do not dispose of batteries in normal family waste. Please recycle, take to a proper battery disposal facility, or contact your local waste disposal supplier relating to native restrictions on the disposal or recycling of batteries. O NOT mount the Sensor inside four ft (1.2 m) of HVAC vents or light bulbs installed below the ceiling line. Hotter rooms could reduce the Sensor’s potential to detect occupants. Use only high-quality lithium batteries, size CR123, 3 V (ANSI-5018LC, IEC-CR17345). Do not use rechargeable batteries. Utilizing improperly rated batteries might damage the Sensor. For questions regarding the installation or operation of this product, name the Lutron Technical Assist Middle. Please present exact model quantity when calling. U.S.A. and Canada (24 hrs / 7 days) Setting the Occupancy Gentle Stage (occupancy version, dimming units only) the Sensor to the mounting bracket by inserting and twisting in a clockwise 2.5 Attach route until the Sensor locks into place. Sensor protection and wireless communication checks as described in 2.6 Carry out sections E. Testing Sensor Protection and F. Testing Wireless Communication. The Sensor ought to be put in in a location the place it has a superb view of all components of the room. The Sensor requires line of sight to operate correctly. If you can not see the Sensor, it can't see you. The Sensor cannot see by glass objects akin to patio or shower doors. The vary and efficiency of the RF system is highly dependent on a variety of complicated elements corresponding to: · Distance between system parts · Geometry of the building construction · Building of walls separating system elements · Electrical tools positioned near system parts Technical Assistance 2.2 Identify a location on the ceiling where the Sensor will have a great view of the room. 2.Three Remove the black "wall side" liner from the adhesive strip. The Sensor is designed for ceiling use solely. Do not install on ceilings increased than 12 ft (3.7 m) or non-ceiling surfaces. Doing so could considerably inhibit the Sensor’s efficiency. 4. Don't paint Sensor. · · · · The "Lights On" and "Lights Off" buttons ought to now switch the lights within the room on and off, respectively, when pressed. Repeat the above procedure to set up the Sensor with any further gadgets. The Sensor is intended for indoor use only. Operate between 32 °F and 104 °F (0 °C and 40 °C). 1.1 several seconds. Sensor that has been arrange. After roughly 6 seconds, the lens will flash rapidly several instances, indicating the sunshine degree has been saved. All Sensors arrange with the Dimmer will now use the saved occupancy light stage. 2. Clean Sensor with a gentle damp cloth only. Don't use any chemical cleaners. Observe: This equipment has been examined and found to comply with the bounds for a category B digital device, pursuant to half 15 of the FCC rules. These limits are designed to provide affordable protection towards dangerous interference in a residential installation. This equipment generates, uses and might radiate radio frequency vitality and, if not put in and used in accordance with the directions, might cause dangerous interference to radio and tv reception, which may be decided by turning the tools off and on. The user is inspired to try to correct the interference by a number of of the next measures: Reorient or relocate the receiving antenna. Increase the separation between the equipment and receiver. Connect the equipment into an outlet on a circuit totally different from that to which the receiver is linked. Consult the vendor or an experienced radio/Television technician for assist. Caution: Adjustments or modifications not expressly authorised by Lutron Electronics Co. could void the user’s authority to function this gear. This gadget complies with Part 15 of the FCC rules. This system should settle for any interference acquired, together with interference that will cause undesired operation. Change 2.1 Set the Dimmer to the specified gentle level for coming into the room. 2.2 Save holding the "Lights On" button on the entrance of a Be aware: For either Sensor version, the lights can also be manually turned off at any time by utilizing the dimming or switching system instantly. Essential Notes or Add the Sensor to the Dimmer or Change by pressing and holding the "Lights Off" button on the front of the Sensor for approximately 6 seconds until the lens flashes briefly. The lights within the room can even flash 3 instances, indicating the Sensor has been successfully added. The Dimmer or Switch will exit set-up mode routinely. The sensitivity of the Sensor might be adjusted based mostly on the anticipated level of activity within the room. There are three available exercise settings: Low Activity, Medium Exercise, and High Activity. Everlasting Drop Ceiling Mounting Note: Go away the removing tab exposed previous the edge of the bracket so it can be accessed for removal later. 6 seconds till all LEDs on the device start flashing. Release the faucet button. Sensor is detecting motion in areas that are not desirable, such as hallways or adjacent rooms, refer to section I. Lens Masking. If Sensor detection is satisfactory during this check, carry out the wireless communication check as described in section F. Testing Wireless Communication. Testing Wireless Communication This check ought to be performed to verify that the Sensor has been appropriately arrange with the corresponding dimming or switching machine and that there's correct wireless communication from the chosen Sensor location. If the lights within the room will not be on, turn them ON manually at the dimming or switching machine. Press and launch the "Lights Off" button on the entrance of the Sensor. The lights should turn OFF. Press and launch the "Lights On" button on the entrance of the Sensor. The lights ought to activate. If the lights don't respond appropriately, confer with the Troubleshooting section. Low light: The lights will solely turn on routinely upon entry if there will not be already sufficient ambient gentle in the room. Hallway falls within Sensor’s coverage area. Disable: This setting converts the Sensor to vacancy mode. The lights will not routinely activate but will still automatically flip off after vacancy. The lights have to be manually turned on through the use of the associated dimming or switching gadget. Note: The 15-second vacancy grace period is lively in this mode. Refer to the Sensor Operation part originally of this doc for more particulars. Troubleshooting Symptom Attainable Causes Solution Lights do not turn on when house is occupied. Sensor is just not accurately added to dimming / switching machine(s). Sensor’s Auto-On setting is set to "Low light" or "Disable". The lights had been lately turned off manually and the timeout has not yet expired. Sensor does not have full view of room. Sensor is outdoors wireless range of dimming/switching system. Seek advice from section B. Set-Up. Refer to section H. Advanced Set-Up. Dimming/switching system has been improperly wired. Gentle bulb(s) burned out. Breaker is off or tripped. Sensor’s timeout is too quick for this application. Sensor does not have full view of room. Lens mask is improperly applied. Sensor’s sensitivity is simply too low. Sensor’s timeout has not but expired. An external noise source resembling an HVAC vent is interfering. Discuss with section A. Pre-Installation. Behavior of lights does not match Sensor settings. Sensor protection extends past room perimeter. The supposed setting was not saved. Multiple Sensors are added to a dimming/switching gadget and their settings don't match. Confer with section A. Pre-Set up. Discuss with section C. Sensor Placement or I. Lens Masking. Check with part H. Advanced Set-Up. Refer to section H. Superior Set-Up. Sensor lens doesn't glow in response to motion throughout Sensor coverage testing. Sensor can't see movement on account of obstruction. Room is too massive or oddly shaped. Move Sensor to another location. Check with section C. Sensor Placement. Multiple Sensors could also be needed for full room protection. Attempt transferring Sensor to a new location or lowering sensitivity. Confer with section C. Sensor Placement or H. Advanced Set-Up. Lights flip OFF while space is occupied. Lights stay ON after house is vacated. Lens does not stop glowing during Sensor coverage testing even when there isn't a movement. Lights don't reply appropriately throughout wireless communication testing. Sensor lens flashes and lights do not turn on when space is occupied. Battery has been installed incorrectly. An exterior noise source resembling an HVAC vent is interfering. Confer with section C. Sensor Placement. Refer to section C. Sensor Placement or F. Testing Wireless Communication. Confer with section H. Superior Set-Up. Refer to part C. Sensor Placement. Check with section I. Lens Masking. Discuss with section H. Advanced Set-Up. Refer to part H. Advanced Set-Up. Try shifting Sensor to a new location or decreasing sensitivity. Check with part C. Sensor Placement or H. Superior Set-Up. Sensor shouldn't be appropriately added to dimming / switching system. Sensor is exterior wireless vary of dimming/switching system. Consult with section B. Set-Up. Transfer Sensor closer to dimming/switching gadget and retry check. Check with section F. Testing Wireless Communication. Battery has been installed incorrectly. Dimming/switching system has been improperly wired. Gentle bulb(s) burned out. Breaker is off or tripped. Battery is low. Refer to section A. Pre-Set up. Remove sensor from check mode. Discuss with section E. Testing Sensor Protection.